Aquaglobe - 5200
- RO MEMBRANE CLEANER
Aquaglobe 5200 is a highly effective cleaning chemical for Ro Membranes, It very effectively removing deposits including carbonate, silicate Sulphate Phosphate of Calcium, Barium Strontium and Iron Scales.
Aquaglobe 5200 is to be regularly used to clean and preserve RO membrane form Fouling & scaling.
Aquaglobe 5200 can be used alone or in combination with Aquaglobe 5200. If membrane is fouled with colloidal biofilm, oil organics and deposits and to Improve the plant performance and enhance membrane life.
Product Data :
Appearance : Clear Colorless to pale Yellow liquid
PH : Acidic
Density : 1.0 to 1.2
Product Feature :
- Effective on inorganic scale safe to membrane surface.
- Suitable for elevated temperatures up to 50-55o c
- Comparative with sea water, polyamide as the chlorine resistant membrane.
- Removes carbonate sulphates, silicate & foulant scale.
- Removes metal oxide & hydroxyl deposits.
- Easy to handle.
- Ready to use liquid
Dosages depends upon the severity of the membrane fouling. For very badly Fouled membrane use 1:4 dilute solution and use for the cleaning. Generally 2.0-2.5 kg suffices for a single membrane. Aquaglobe5100 is suitable for Cleaning most RO membranes, although the pH should be adjusted for use on CA membranes.
Cleaning Guideline :
Aquaglobe 5200 is recommended to be used in the volume of 25-30 lit to 40-50 lit for a 8”x 40” membrane element.
During cleaning the flow rate should not exceed design limit. Also membrane Cleaning should be carried out at low pressure <60> psi.
Allow the membrane to soak in cleaning solution for minimum 45-60 minutes Between recirculation. This procedure is to be repeated throughout cleaning process Regularly.
While cleaning a multi stage plant, clean each stage individually. Flush pipe work Membrane and cleaning tank thoroughly with chlorine free water between each Cleaning and reflush the plant to normal operation.
Generally most of the cleaners temporarily affect the membrane support structure And it takes routine operation of 5-24 hrs to stabilize the parameters.
keep the container away from direct heat & sunlight. Keep the container Closed when not in use. The product not be swallowed and prolonged contact With the skin should be avoided. Should it come in contact with the eyes flush With clean, cold water and get medical attention.